Straight from the Water Heater Manufacturers
We’re not the only ones who know how important anode rod functionality and replacement is. Virtually every water heater manufacturer talks about it in their product’s use & care manual. Here are some of the highlights.
TECHNICAL SERVICE DEPARTMENT
Technical Service Bulletin
Anode Rods, Cathodic Protection and the Porcelain (glass) Lining
Corrosion can be defined as the destructive attack of a metal by an electrochemical reaction with its environment. Steel exposed to moisture and oxygen will rust and corrode. Corrosion is defined as the "eating away" of metal by electrochemical means. There are four main factors affecting waters ability to corrode:
- Acidity - Water is made acidic by naturally occurring dissolved gases such as carbon dioxide.
- Temperature - Higher temperatures speeds up the corrosive process.
- Amount of dissolved oxygen - Free oxygen dissolved in the water promotes corrosion.
- Electrical conductivity - The more dissolved mineral solids in the water, the greater its ability to carry electrical current. When dissimilar metals are in the water:
- Electrical current flows between metals
- One of the metals gradually corrodes faster than the other
Dissimilar metals are present in the interior steel tank surfaces of all water heaters in several forms such as the drain nipples, heating elements, inlet and outlet nipples, and immersion thermostats. These metals, and others present in the water itself, combined with the oxygen content of the water and heat, establish an environment conducive to corrosion. The dissimilar metals create a corrosion cell that is enhanced by the conductivity of the water. The anode is installed to overcome (neutralize) the corrosive cell.
The Porcelain (glass) Lining
In a water heater, corrosion is protected by a glass (actually a porcelain enamel) lining in the steel tank, and the use of auxiliary anode rods. Porcelain enamel begins as a blend of minerals mixed in a manner to form liquid slurry. This slurry, resembling a thin mud, is sprayed onto the inner surfaces of the water heaters. During the manufacturing process, the inside water tank and both the top and bottom heads are sprayed with a slurry of glass material. After the tanks are sprayed, they are fired at very high temperatures - generally ranging from 1500 to 1600 degrees Fahrenheit. While in the furnace the porcelain bonds with the metal to create more than a coating. It forms an inseparable compound merging the chemical make-up of the porcelain glass lining and metal resulting in a new, chemically unique finish.
This glass provides a long life to the steel tank; otherwise, the tank would fail or corrode in a relatively short time. Every glass lined water tank, no matter how carefully it is manufactured, has some microscopic bare metal areas exposed to the water inside the tank. There is a chance that a crack or chip in the porcelain lining will allow the water to come in contact with the steel tank. Over time, water, a universal solvent that becomes more aggressive with temperature, slowly dissolves the interior tank lining. This will create conditions for corrosion, pinholes in the tank and finally tank failure.
The life of the anode, in turn, depends on water temperature, amount of water used, and the quality of the glass lining. However, the most important factor in the life of the anode rod is the water chemistry, the hardness or softness of the water. Water softeners contribute to the change in water chemistry. Indirectly, softened water acts to reduce the service life of the anode, since its current demand becomes drastically higher. Also, check the manufacture and installation date of the water heater.
Do not remove the anode rod from the water heaters tank, except for inspection and/or replacement, as operation with the anode rod removed will greatly shorten the life of the glass lined tank and will exclude warranty coverage. The anode rod should be removed from the water heaters tank annually for inspection and replaced when more than 6 inch of core wire is exposed at either end of the rod.
In addition, some of these waters have excessive sulfate content along with various strains of sulfate reducing bacteria (see Document 1206). These bacteria, harmless to health, will grow in the presence of the highly active magnesium anode rod and using the hydrogen ion from the anode-cathode reaction, will produce hydrogen sulfide gas. The gas smells like rotten eggs. The greater the activity of the anode, the more hydrogen ions are produced and the more hydrogen sulfide (smelly) gas. These bacteria can be killed with adequate additions of chlorine, such as with an automatic chlorine feeder.
The R-tech anode rod was developed to operate in a broad range of waters without the sensitivity to the various water conditions. This anode or a variation there of, has been used over 15 years in gas water heaters with minimal problems with odors. With the invention of the resistored electric heating element, Rheem now uses the Rtech anode rod in electric water heaters. In doing this, we are now able to efficiently utilize the R-tech anode in all type of water conditions.
How to Replace the Anode Rod
CAUTION: Draining your water heater for this procedure may put you at risk of being scalded by hot water. Please be careful when working on your water heater.
- Turn the power OFF to the water heater at the circuit breaker (electric heater) or main gas line (gas heater).
- Fasten a length of garden hose to the drain valve at the bottom of the heater. Put the other end of the garden hose in the nearest floor drain or snake it outside the home.
- Close the shut off valve at the cold water inlet line.
- Open the temperature and pressure relief valve at the top of the heater. This will relieve pressure inside the tank. Now open the drain valve and allow about a gallon of the water to drain. You will probably notice some small white particles (called scale or sediment) during the early stages of the flow.CAUTION: THE WATER WILL BE HOT...........BE SURE NO ONE IS NEAR THE DRAIN HOSE OR THEY COULD BE SCALDED.
- After about a gallon of water, close the drain valve and remove the hose. Leave the temperature and pressure relief valve at the top of the heater open for the time being.
- Remove the old anode rod with a 1 and 1/16 inch six-sided wrench or socket. Do NOT use a 12-point wrench or socket or you will strip the head of the anode. Get at least a 24-inch cheater bar. I keep a piece of 3/4 inch black iron pipe in the garage just for this purpose. Place the cheater pipe over the socket handle. Have someone hold the water heater while you slowly break the seal. Once broken, the anode removes quite easily.
- Replace with a new anode rod. It is a 3/4-inch National Pipe Thread (NPT) part. You may find one at any plumbing house or home store. Use pipe sealer or Teflon tape to seal the threads. Snug it down tight. Remember the water heater builds up 150 PSI of pressure inside the tank.
- Open a hot water faucet somewhere in the home. Open the shut off valve at the cold water inlet line. You will hear the heater start to fill.
- When you have a steady stream of water from the temperature and pressure valve tube, close the valve; when you have a steady stream of water from the hot water faucet, turn the faucet off.
- Turn the power ON to the water heater at the circuit breaker (electric heater) or main gas line (gas heater; relight pilot if required). Allow the water heater to recover. Check the anode rod one more time to make sure it is tight and there are no leaks.
The anode rod should be removed from the water heater’s tank annually for inspection and replaced when more than 6″ of core wire is exposed at either end of the rod.Sourced From Rheem / Electric Residential Water Heaters Use and Care Manual AP9029-9
The anode rod should be removed from the water heater tank every 3 years for inspection. The following are typical (but not all) signs of a depleted anode rod:
- The majority of the rods diameter is less than 3/8”.
- Significant sections of the support wire (approx. 1/3 or more of the anode rod’s length) are visible. If the anode rod shows signs of either or both it should be replaced.
Installation Instructions and Use & Care Guide for Residential Gas Water Heaters 186486-002
A. O. Smith
Anode Rod Inspection
The anode rod is used to protect the tank from corrosion. Most hot water tanks are equipped with an anode rod. The submerged rod sacrifices itself to protect the tank. Instead of corroding the tank, water ions attack and eat away the anode rod. This does not affect the water’s taste or color. The rod must be maintained to keep the tank in operating condition.
NOTE: Artificially softened water is exceedingly corrosive because the process substitutes sodium ions for magnesium and calcium ions. The use of a water softener may decrease the life of the water heater tank.
Anode deterioration depends on water conductivity, not necessarily water condition. A corroded or pitted anode rod indicates high water conductivity and should be checked and/or replaced more often than an anode rod that appears to be intact. Replacement of a depleted anode rod can extend the life of your water heater. Inspection should be conducted by a qualified technician, and at a minimum should be checked every three years. Typical (but not all) signs of a depleted anode rod are as follows:
- The majority of the rods diameter is less than 3/8”
- Significant sections of the support wire (approximately 1/3 or more of the anode rod’s length) are visible. If the anode rod shows signs of either or both it should be replaced.
NOTE: Whether re-installing or replacing the anode rod, check for any leaks and immediately correct if found.Sourced From A O Smith - Instructions Manual Residential Electric Water Heaters 185762-002
The anode rod should be removed from the water heater tank every 3 years for inspection. If the rod is more than 50% depleted, the anode rod should be replaced.Sourced From American National Standards Institute / Residential Electric Water Heater Installation Instructions and Use & Care Guide 6510236
A combination sacrificial anode rod/hot water outlet nipple has been installed to extend tank life. The anode rod should be inspected periodically (every 2 years) and replaced when necessary to prolong tank life. Water conditions in your area will influence the time interval for inspection and replacement of the anode rod. Contact the plumbing professional who installed the water heater or the manufacturer listed on the rating plate for anode replacement information. The use of a water softener may increase the speed of anode consumption. More frequent inspection of the anode is needed when using softened (or phosphate treated) water.Sourced From Bradford White - Electric Water Heaters Installation
Operating Instruction Manual 238-44422-00H
Anode Rod Inspection
The anode rod is used to protect the tank from corrosion. Most hot water tanks are equipped with an anode rod. The submerged rod sacrifices itself to protect the tank. Instead of corroding the tank, water ions attack and eat away the anode rod. This does not affect the water’s taste or color.
The rod must be maintained to keep the tank in operating condition. Anode deterioration depends on water conductivity, not necessarily water condition. A corroded or pitted anode rod indicates high water conductivity and should be checked and/or replaced more often than an anode rod that appears to be intact. Replacement of a depleted anode rod can extend the life of your water heater. Inspection should be conducted by a qualified technician, and at a minimum should be checked annually after the warranty period.Sourced From State Water Heaters
Technical Service Instruction Manual for Residential Gas Water Heaters 184115-000 0 3 -03